The chiller maintenance tool that contributes most to a chiller's overall efficiency is the daily log.
We have one in our
Air Conditioning and Refrigeration System Evaluation Manual,
and there are also cycle diagrams, and guidance for evaluating chiller operating pressures and temperatures.
An accurate daily log will provide a daily snapshot of the chillers operating characteristics.
This makes abnormal conditions easy to spot, so corrective action can be taken before problems get serious and expensive.
What kind of checks should a chiller maintenance program include?
Periodically, and before the cooling season, you have to check the chiller starter and controls.
Make sure theres no litter, dirt, or debris in the panels.
Make sure all the linkages move freely.
Make sure the overloads are set correctly and that they work,
make sure all wiring connections are tight,
and check all contacts for pitting and corrosion.
Verify that the safeties and controls all work.
Of course, chiller maintenance requires careful periodic inspection of the compressors.
Look for signs of overheating, look for oil leaks, and check the motor terminals for pitting, corrosion, or loose connections.
Make sure the crankcase heaters are working properly.
Check the compressor oil level and oil filter, and follow the manufacturer's guidelines about the frequency of changing them out.
Another important chiller maintenance procedure is to follow the manufacturer's guidelines about having an oil sample analyzed for destructive acids and corrosive materials; and having the oil filter analyzed for metal deposits.
It's also a good idea to have a refrigerant sample analyzed periodically to see if there's moisture, acid, or rust present.
The oil, filter, and refrigerant analysis will give you a good picture of the chiller's condition, and will help you schedule corrective action if it's needed.
Of course, check operating pressures and temperatures, and evaluate whether or not the chiller has a full refrigerant charge.
Air Conditioning and Refrigeration System Evaluation Manual
has cycle diagrams of air-cooled and water-cooled chillers, and guidelines on evaluating chiller operating pressures and temperatures.
Air cooled chiller maintenance will include cleaning the condenser coils, and verifying that the condenser fans are all working properly.
A very effective predictive maintenance procedure is eddy current tube testing.
A trained technician runs a small electric current through each tube and analyzes the current flow.
Eddy current testing of the chiller tubes can help identify internal pitting, freeze damage, support wear, zipper cracks, and corrosion.
It's recomended at intervals of 3 to 5 years, and can be done by a trained technician in two or three days.
It can help indicate corrective repairs that will prevent major breakdowns.
I hope this page has helped you understand some of the essential chiller maintenance procedures, and please, feel free to contact us with any specific HVAC questions you might have, including questions about air conditioning on Guam, and refrigeration on Guam.
For a detailed guide on your specific installation, contact your chiller's manufacturer, and follow their recommendations.
Are you learning the HVAC Trade "on the job"? |
If you would be interested in developing your potential to become the finest HVAC Technician you possibly can by studying a complete, accredited HVAC Technician course at home; we highly recommend that you contact Penn Foster Career School and request their free, no-obligation information brochure.
Requesting the information is easy and only takes 2 minutes; and it might be the first step towards changing your whole future.
You'll find a brief review of the course on our HVAC Training page.
Return from Chiller Maintenance to the Air Conditioning and Refrigeration Guide home page.